Fire Compliant Containment System
- Fire Activation Control Kit Mechanism shall be placed near BMS Panel the same shall be connected with Fire Control Panel. With use of Hardware and Software Integration the Roof Panels/Doors would open in case of fire.
- The configuration can be changed as per requirement
CAC Top Panel Magnetic opening kit The top panel falls open after getting sudden air pressure from the top side. The same is dependent on the sudden air pressure release from the FM-200 nozzle. The opening action is based on multiple site conditions during an actual scenario
EML Drop Panel
The top panel falls open after the signal is received from the fire controller. It shall swing open to approximately 70 degrees upon activation. The time required will be less than 10 seconds. The same shall be based on an electromagnetic system with redundancy. The panel has to be closed manually by pushing it up until it locks after activation. The panel shall be at some height above the top panel as per the site condition, with an opening of approximately 6 sq ft.
Motorised Drop Panel
Top panel auto-opening kit, which opens after a signal is received from the fire controller. It shall swing open to approximately 80 degrees upon activation. The time required will be less than 10 seconds. The same shall be based on a motorised system with redundancy, assuming 2 panels with automatic closing., The panel shall be approx. 100 mm above.
Power Kit For BMS Fire Integration of all Top Panel systems to Integrate with Fire Unit